Failure of the bonding connection caused damage to a single-family dwelling
July 17, 2020
Regulated industry sector: Electrical - Low voltage electrical system
Due to the poor bonding connection made by the loose locknut and oversized knockout for the connector, the bare conductor and metal connector arced until the bonding path failed. This failure occurred before and without the supply utilities overcurrent protection clearing the fault.